Rebel Brewer Giveaway!
 Home Brew Forums > Big TX Home Brew E-Herms Build Out

12-06-2011, 02:40 AM   #21
hatrickwah
Vendor
Feedback Score: 1 reviews

Recipes

Join Date: Nov 2010
Location: The Woodlands, TX
Posts: 263
Liked 6 Times on 5 Posts

Quote:
 Originally Posted by P-J Would this diagram help you? (As always - click on the image to see a full scale diagram that is printable on Tabloid paper 11" x 17")
Thanks P-J, I was using yours from Tiber_brew's build. Honestly, both are working for me. I'm trying to keep the switches and LEDs to a minimum with this build. For instance, I don't want the function of being able to turn the element on and by-pass the BCS controller (if my wife brews, I can already hear the element popping in my mind). I'll also be programming BCS such that it won't fire both elements at the same time, but if it becomes an issue, I can always replace the ones I bought with smaller ones so the 50a circuit can handle it easily.

The question from 52pickup brings up one I had, do I need to go with 25a or 30a breakers for the elements? I just checked my wall power, turns out TX may be kicking out a little extra voltage, I was showing 130v (260v?) on my meter (steady). I'll double check at the panel later on my a/c circuit.

__________________

Keeping busy brewing & building.

Electric Brewing Supply

My e-Brewery | Keezer Build & Tap Tower Refurbish |Glycol System

12-06-2011, 02:47 AM   #22
P-J
Feedback Score: 0 reviews
Recipes

Join Date: Mar 2010
Location: Charlotte, NC
Posts: 3,010
Liked 206 Times on 165 Posts
Likes Given: 326

Quote:
 Originally Posted by 52pickup Ok... a 240v 5500w element averages 23a. I don't know about your neck of the woods, but at my house my "240" line averages closer to 220 actual volts. So, 5500w/220v= 25a = popping breakers everytime you blink.
It does not work that way.
A 240V 5500W element on 220V will draw less than 22A.

Ohms Law.!!!!

__________________

12-06-2011, 02:58 AM   #23
hatrickwah
Vendor
Feedback Score: 1 reviews

Recipes

Join Date: Nov 2010
Location: The Woodlands, TX
Posts: 263
Liked 6 Times on 5 Posts

The advertised wattage is the optimal wattage at the desired 240v draw based on the resistance of the element. The element is actually stamped with 5500w at 240v, 4000w at 208v, so...

The irony is, the breakers are the same price whether I choose 25a or 30a. Its really a question of how close to cut it. I'm leaning to the 30a but feel more comfortable with the idea of the 25a, but I say that knowing I also have the 50a GFI on the back end as well. I'll likely go 25a.

__________________

Keeping busy brewing & building.

Electric Brewing Supply

My e-Brewery | Keezer Build & Tap Tower Refurbish |Glycol System

12-06-2011, 03:10 AM   #24
52pickup
Feedback Score: 0 reviews
Recipes

Join Date: Dec 2010
Location: Tucson, AZ
Posts: 56
Liked 2 Times on 2 Posts

Touche'

Too many beers for me - got my ohms, watts and such all discombobulated.

However, if the OP says he is showing closer to 260v - that would put him at alomst 25a - no?

__________________

Primary 1: Hurricane IPA
Primary 2: Empty
Kegged: BM's Centennial Blonde(round 2)
Falconers Flight Black IPA
Bottled: SAKE!

12-06-2011, 03:12 AM   #25
hatrickwah
Vendor
Feedback Score: 1 reviews

Recipes

Join Date: Nov 2010
Location: The Woodlands, TX
Posts: 263
Liked 6 Times on 5 Posts

Quote:
 Originally Posted by 52pickup Touche' Too many beers for me - got my ohms, watts and such all discombobulated. However, if the OP says he is showing closer to 260v - that would put him at alomst 25a - no?
That's what has me still pondering tonight. I'll check the panel tomorrow. I still have time, nothing ordered yet.
__________________

Keeping busy brewing & building.

Electric Brewing Supply

My e-Brewery | Keezer Build & Tap Tower Refurbish |Glycol System

12-06-2011, 03:21 AM   #26
P-J
Feedback Score: 0 reviews
Recipes

Join Date: Mar 2010
Location: Charlotte, NC
Posts: 3,010
Liked 206 Times on 165 Posts
Likes Given: 326

If you are receiving 260V on your lines, you NEED to call your power company. That is a real problem with THEM.! Be sure to measure your voltage between the 240V posts in the breaker box.

__________________

12-06-2011, 03:26 AM   #27
hatrickwah
Vendor
Feedback Score: 1 reviews

Recipes

Join Date: Nov 2010
Location: The Woodlands, TX
Posts: 263
Liked 6 Times on 5 Posts

Quote:
 Originally Posted by P-J If you are receiving 260V on your lines, you NEED to call your power company. That is a real problem with THEM.! Be sure to measure your voltage between the 240V posts in the breaker box.
That's where I'll head tomorrow. Definitely wouldn't want to be out there today, just a bit of rain in the past 24 hours.
__________________

Keeping busy brewing & building.

Electric Brewing Supply

My e-Brewery | Keezer Build & Tap Tower Refurbish |Glycol System

12-06-2011, 03:31 AM   #28
P-J
Feedback Score: 0 reviews
Recipes

Join Date: Mar 2010
Location: Charlotte, NC
Posts: 3,010
Liked 206 Times on 165 Posts
Likes Given: 326

Yes. Do not do that in the wet and also in the dark. Not worth the risk.

Please let us know what you measure. (I'm interested.)

P-J

__________________

12-06-2011, 06:44 PM   #29
audger
Feedback Score: 0 reviews
Recipes

Join Date: Apr 2011
Location: ., Connecticut
Posts: 1,477
Liked 35 Times on 35 Posts
Likes Given: 1

Quote:
 Originally Posted by hatrickwah The irony is, the breakers are the same price whether I choose 25a or 30a. Its really a question of how close to cut it. I'm leaning to the 30a but feel more comfortable with the idea of the 25a, but I say that knowing I also have the 50a GFI on the back end as well. I'll likely go 25a.
choose whatever size breaker that your wiring can support. if your wire size can only support 25A before overheating past a point where you are comfortable, then that is the breaker you use. if your wire can handle 30A, use that breaker. it has nothing to do with any particular device you are connecting to it. a breaker is meant to protect the wiring from melting in the event you draw too much current. underprovisioning is a waste of money (well maybe not if they are the same price, but still...), and overprovisioning subverts the entire function of having circuit protection.
__________________

12-06-2011, 08:38 PM   #30
hatrickwah
Vendor
Feedback Score: 1 reviews

Recipes

Join Date: Nov 2010
Location: The Woodlands, TX
Posts: 263
Liked 6 Times on 5 Posts

Quote:
 Originally Posted by audger choose whatever size breaker that your wiring can support. if your wire size can only support 25A before overheating past a point where you are comfortable, then that is the breaker you use. if your wire can handle 30A, use that breaker. it has nothing to do with any particular device you are connecting to it. a breaker is meant to protect the wiring from melting in the event you draw too much current. underprovisioning is a waste of money (well maybe not if they are the same price, but still...), and overprovisioning subverts the entire function of having circuit protection.
At the moment nothing has been bought, but now that you bring up wire. I'm getting mixed information, and not sure how I want to procede. I plan to use 8awg stranded between the breaker and the spa panel, 30ft, outside in conduit, or at least that was the plan. If you research the wire, manufacturers and retailers all vary.

__________________

Keeping busy brewing & building.

Electric Brewing Supply

My e-Brewery | Keezer Build & Tap Tower Refurbish |Glycol System