One thing to be sure of is that the hot and neutral of each circuit MUST be kept completely separate from the other circuit. IOW, the hot from one circuit CANNOT use the neutral of the other circuit as a return. GFCIs monitor the current in the hot and neutral path and trip if they are not exactly equal.
Rearranger IPA - Chinook, Simcoe, Cascade
Ponchy Pale Ale - Millennium and Willamette
NippleRub Ultra (Light Lager w/Mexican Lager yeast)
In the Chamber:
A Light Lager