Originally Posted by Chugmaster
If you have three GFI breakers, that means that there are technically three 10awg grounds coming out of your box, correct?
If you use cable like romex for the feeds, you need to carry an equipment ground in each cable. If you run the feeds in conduit, you size the equipment ground (only one is required) for the largest circuit breaker. All simply get tied together and bonded to the control panel.