My apologies in advance for my drawing. Most diagrams on this forum are outstanding; mine, maybe not so much.
I have main power going in to a switch and then to a distribution block. I have three loads from that block. One to an outlet, one to a switch for the pump and element (set up so the element can't run without the pump being engaged) and one for the PID. All grounds are attached together.
The switch from the pump provides a load to the switch for the element. The power runs from that switch, to the SSR, through an indicator light and finally to power out.
Everything appears to work. When I put a receptacle tester in the element outlet, it operates as it should. When I plug a lamp in, it will not light up.