Originally Posted by lschiavo
Most lugs are not rated for more than one conductor so adding another tap to your feed through lugs may not be correct. You could replace the stove panel with a small load-center and gain a few future breakers while at it. Six service disconnects is the rule. You have two now if I understand correctly.
That's probably what I'll wind up doing, just means I need to upgrade to thicker copper feeding the sub panel. I had some 10G around and was trying to save time. Only in the house another year so trying to minimize my investments.
Also, if I'm going to go with the switch would it make more sense to put it upstream of the PID? That way when I cut the power with the switch it kills the PID and the element at the same time.