so i go to test my control panel for the first time plug it it turn the switch and nothing... better than smoke but as it turns out i mistakenly got the wrong contactor. i had them wired as being 24v coils instead they are 220v. 120v will move the coil but it bounces like crazy and makes an awful racket.
So what I have is a 50amp service coming to the box and each leg going through a contactor. What is a good single contactor that can handle 50 amps and is quiet that runs on 120v. One of the benefits of moving to electric was being quiet.
Would this be the way to go?
Any advice would be greatly appreciated.