Originally Posted by jfkriege
I thought the ground and neutral were tied together at the box and so functioned as either.
You are right, ground and neutrals are common in the panel, they are on the same bars... but
You cannot run a ground wire as a neutral, and a ground in your system. Otherwise, there would be no neutrals in your home. The electic guys are going to be all over this, any bet on how long?