Originally Posted by lonepalm
I will once i get home this evening. I was really looking to getting a definition of what each setting was....
it is in F
I'll also take a pic of my wiring diagram
ROFL after looking through about 50 pages. I found the manual on page 249, going to confirm connections and set accordingly.
With my posts per page settings there are only 34 pages in this thread for me, so I'm not sure which manual you're looking at. Most of this thread is in reference to the STC-1000, which has different wiring and different programming than the unit you have, so the manual you found may or may not be helpful. Just in case the manual you found isn't the correct one for your unit, here's a diagram and some programming instructions-
Press the SET key once to enter the control temperature setting, press ▲ or ▼ keys to adjust your set point temperature. Press SET button again to exit setting mode.
Press and hold SET button for three seconds to enter the system menu settings, press ▲ or▼ button to select the menu, press the SET button once to enter the appropriate parameter settings, press ▲ or ▼ button to modify the parameters.
After adjustment, you can exit by pressing the RST key, or by waiting for 5 seconds.
HC Heating or Cooling mode control
d Temperature differential
LS Minimum set limits
HS Maximum set limits
CA Tempreature calibration
PT Compressor delay
The compressor delay comes factory set to 1 min, so if you weren't waiting 1 min for the relay to activate after turning the unit on, that very well could have been your problem. Once you get it up and running, I'd suggest putting the compressor delay at the max setting (10 min) to protect your compressor from short cycling.
Hope this helps.