Last Activity:07-02-2015 11:35 AM
Likes Given: 133
92 Likes on 80 Posts
Posted in thread: I want short lines.... how? on 06-29-2015 at 03:50 PM
FWIW, a quick calculation puts 2.2 fluid ounces in 12 feet of 3/16 ID line.
Posted in thread: I want short lines.... how? on 06-29-2015 at 02:52 PM
.....Seems the beer in the lines goes flatish over a few days so the first 1/3? or so of a new
pour isnt carbed the way i like it and as such the first beer seems flatter than i like unless
i dump it ...
Posted in thread: I want short lines.... how? on 06-29-2015 at 01:42 PM
IMO, drinking an undercarbed 1/3 pint seems like a small price to pay. Maybe flow control
faucets are an option?
Posted in thread: Another NEMA 10-50 3-wire Dryer/Range Thread... on 06-25-2015 at 10:54 PM
IMO, if all three of the existing conductors are #6 copper, you can add a #10 copper ground, a
14-50 receptacle, and have a 50amp/4-wire circuit. The neutral should be terminated on the
neutral buss b...
Posted in thread: Question on wiring for 2-stage Inkbird in Collar on 06-24-2015 at 08:20 PM
That was another concern. When you say switched hots you mean line 5 and 6 right (heating and
cool powers)? And line 2 would be fine to be ran this way?I guess that means longer single
wires that I ma...
Posted in thread: Question on wiring for 2-stage Inkbird in Collar on 06-24-2015 at 05:00 PM
That top blue wirenut looks suspect. The switched hots need to be independently fed back to the
heat and cool receptacle hot terminals. The only neutral to the controller is for AC to the
Posted in thread: Thermostat temperature swings due to differential setting on 06-22-2015 at 04:21 PM
I position the sensor on the exterior of my glass fermenter, under a piece of closed cell pipe
insulation. I have verified that it reads the wort temperature. The wort temperature is what we
Posted in thread: my beer is just dripping out? on 06-18-2015 at 12:17 PM
.... its only like a 5ft beer line too, but that shouldnt matter right? ....This might not
matter in relation to the likely clog but it will certainly matter once beer is flowing freely.
Rule of thumb...
Posted in thread: How many freezers do you have? on 06-16-2015 at 11:33 AM
Six refrigerating appliances:Garage:True GDM-12 with 4 corny kegs and faucetsTrue GDM-10 for
fermentation modified with STC1000 type controllerTrue GDM-6 for yeast bank, starter crashing
and supplies ...
Posted in thread: 4 Prong Outlet for Hosehead Question on 06-13-2015 at 02:19 PM
Hi everyone,I have installed a 4 prong outlet that is GFCI protected through a breaker in my
main panel. The breaker tests just fine and only trips when I've commanded an element to on.