Last Activity:08-05-2014 9:31 AM
Posted in thread: Converting "True" brand keg system to 2 compartments on 10-30-2013 at 02:32 AM
Hey everyone. I've done some searches but came up blank. Has anyone ever converted a 1
compartment system such as the "true" TDD-4 system to be able to set to 2 different
temperatures?I have a chance ...
Posted in thread: Can I reuse this yeast? on 07-27-2013 at 11:14 PM
ok i'll sanitize very well and buy some new yeast tomorrow, rather be safe than sorry.
Posted in thread: Can I reuse this yeast? on 07-27-2013 at 10:58 PM
That's fine I think I can separate it, but will it be ok for the wort to sit 24hrs without
yeast in my primary bucket w/ airlock?
Posted in thread: Can I reuse this yeast? on 07-27-2013 at 10:30 PM
So when I did my first batch of IPA a couple months ago I apparently visited a bad website on
how to reuse yeast because it said to just put what's left after racking into plastic bottles
and to just ...
Posted in thread: Auto Tuning on 05-25-2013 at 09:45 PM
Got it to work somehow. I think starting the auto tune and then going back to the auto/manual
setting and setting it to 1 did the trick but I'm not 100% sure.Anyway, first brew day is done!
I think I ...
Posted in thread: Auto Tuning on 05-25-2013 at 01:32 PM
Hi all,I have the auber syl 2352 PID and I'm trying to autotune on my electric setup. The "out"
light flashes and cuts power every 2 seconds or so but the temperature just keeps rising during
Posted in thread: GFCI would not trip with test button on 05-01-2013 at 08:02 PM
had e same issue except I have a Midwest panel. I called GE and they sent a replacement
breaker. I haven't tested it yet though. Hoping it was faulty.
Posted in thread: SSR and contactor confusion on 04-22-2013 at 07:21 PM
The mechanical contactor is not switched by the SSR, the contactor opens and closes the circuit
that runs between the SSR and the element.You run the load wire out of the SSR to the line side
Posted in thread: Yet Another eBIAB Build on 04-22-2013 at 05:59 PM
You were right in what you said, your 30a main panel breaker is 2 hots. You should have a
neutral (white) bus bar in your main panel where all the white wires from your whole house
connect to. Same wi...
Posted in thread: Chugger Pump Prongs on 04-17-2013 at 12:51 AM
Hey all,Looking for a gut check here. The cord on the chugger pump is a bit short to reach my
panel so I decided to make a simple extension cord. Normally the hot wire is on the right side
of the plug...