Originally Posted by pp270
I see and then the neutral pigtails on the GFIs are then connected to the neutal bar in the panel.
Are you running just the two hots and ground to your brew rig or all four two hots, ground, and neutral?
2 hots, ground and neutral. Yes, the load hots go to the GFCI hots, the load neutral goes to the GFCI neutral terminal, the load ground goes to the common neutral/ground bar. The GFCI pigtail goes to the common ground/neutral bar