Originally Posted by skipper1953
I don't mean to start an argument but, I've been under the impression that you should never put a switch in a neutral line. I'm sure someone more fluent in electricianese can explain whether I have been mislead or not.
Yeah, I'm not an expert either but what you're saying makes sense...and I've heard (read) that in other places. As such, I decided not to switch any of my neutral lines. So, my contactors are double pole, but I'm only using 1 of the poles on each contactor (for the hot line).
I'm about 95% finished wiring everything up...when complete, I'll post some pictures, along with the schematic that I used as reference.