Originally Posted by thargrav
The white wire running from one of the breaker out terminals to the neutral bus is probably what's tripping your breaker.
Thanks. I will take care to clean up the wiring.
As for the white wire going to the neutral bus. This is the wire that came pre-installed on the breaker.
According to this P-J diagram I thought it needed to be attached to the neutral bus. Is this not the case?