||04-02-2010 10:11 PM
So I've got the 40A subpanel in my laundry room already. I can run 8/4 over to my brew panel and divvy the power up there, as so:
Or run 8/3 for the 220 outlets and 12/2 for the 110 ones. Either way the wiring in the brewery panel will be the same, the power will just come from a different place.
Now if I've got things GFCI protected and have access to the breaker, is there a reason to be breaking both legs of the heating element plugs, either with another SSD or a hard switch?
edit: fixed the attachment
Copyright ©2000 - 2014, Jelsoft Enterprises Ltd.