Asking question...not looking for attacks. The cost of safety is priceless...but here is a question. A 30A 240V GFCI Breaker is roughly $120. A 50amp spa box is $69 at Home Depot.
If i were to run a 30A 2 pole breaker (Non-GFCI) in my Electrical panel, feeding a 10/3 line connected to a 50a GFCI Spa box. Would this in theory and safety, work?
My thought is would have the GFCI at "Wet" end and would have a 30amp feed from origin (electrical panel).